The fire rated uninsulated access door can be used on fire rated walls.
16 gauge cold rolled steel
Continuous piano hinge. Hinge location: Hinges must be located on the second dimension (height).
Self-latching tool-key operated slam latch and ring operated slam latch, both included.
1" exposed flange
2½ " in depth, made of cold rolled steel
Door sizes + ¼" or + 6mm
Mechanisms to allow panels to open from inside, standard on all doors over 12" X 12 inches.
High quality white powder coat primer.
Individually wrapped, 1 door per box.
Fire rated access doors, for vertical use, are subject to the following:
UL 10B (2009), NFPA 252 (2012), CAN/ULC S104 (R1985), CAN/ULC S104 (2010).
1-½ hours, neutral/negative pressure
36" x 36" (914 mm x 914 mm), maximum area of 1296 in², tolerance on height and width limitation is more or less 3" (76mm) as long as the area does not exceed 1296 in².
No rating achieved
The fire rated insulated access door can be used on fire rated walls and ceilings. The drywall bead flange is not exposed once the drywall compound is applied.
The fire rated insulated access door can be installed on fire rated walls and ceilings.